Dry Risers Installation
What are Dry Rising Mains?
A dry rising main is a system of pipe work and valves, often found in high-rise buildings, which allows fire fighting water to be easily delivered to all floors. It consists of a vertical pipe with an inlet at ground level on an outside face of the building and outlets (known as landing valves) fitted in cabinets at each floor level, allowing fire and rescue service personnel to pressurise the main from their appliances.
The installation of a riser removes the need for firefighters to have to drag charged fire hoses through the building to the upper floors. This would delay fire-fighting operations and create a hazard during evacuation.
Where do dry risers have to be installed?
Approved Document B (Fire Safety) of the Building Regulations requires that any building more than 18m high, measured from the fire brigade access level to the top floor. When a building is over 50m then a wet rising main will need to be installed.
Dry Rising Mains Operation
The pipes in dry risers are empty and are only filled with water by fire fighters on their arrival at the incident. Fire fighters will connect the fire appliance pump to the dry riser inlet via two lengths of 70mm hose.
The dry riser is then charged with water from the fire engine, the fire engine water supply is augmented from the nearest fire hydrant.
Fire Fighters take fire fighting hose to the floor below the fire and connect this hose to the landing valve, the hose is connected via a 65mm instantaneous coupling and a fire fighting branch connected to the other end of the hose.
The landing valve is then opened to allow the water in the dry rising mains to charge the fire fighters hose, enabling the fire to be fought. The fire appliance pump ensures the correct flow and pressure of water is supplied to the floor of the fire.
Fire Service Inlets
The dry riser inlet is installed at the fire brigade access level. This breeching connection is usually housed in a red glass fronted box with the wording ‘Dry Riser Inlet’. This inlet should be positioned as close as possible to the rising main in order to reduce pressure losses. The inlet box and breeching inlet should be installed with the lower edge of the box between 400mm and 600mm above the ground.
The valves are fitted with a wheeled valve connected directly to a 65mm instantaneous female coupling with a removable blank cap and retaining strap. They are installed at each floor level except the ground floor and should preferably be housed in a red lockable box marked ‘Dry Riser’
For further information or quotation please contact us.